# Anchor Fault Identification Method for High-Voltage DC Submarine Cable Based on VMD-Volterra-SVM

^{1}

^{2}

^{*}

## Abstract

**:**

## 1. Introduction

## 2. VMD-Volterra-SVM Algorithm

#### 2.1. VMD Principle

#### 2.2. Principle of the Volterra Model

#### 2.3. SVM Principle

#### 2.4. VMD-Volterra-SVM Algorithm Flow

## 3. Simulation Analysis

#### 3.1. Finite Element Model Building

^{3}, projection of the anchor bottom against the water surface to A = 0.048 m

^{2}, seawater density to ρ

_{w}= 1030 kg/m

^{3}, seawater resistance coefficient to C

_{D}= 1.1, medium gravity acceleration to g = 9.8 m/s

^{2}, velocity of the anchor striking the cable to v, ignore the influence of sea tide on the anchor, and use the motion equation of a ship anchor in the process of falling, which is as follows:

^{2}is applied to the entire model, and a downward velocity $v$ is applied to the anchor separately. In this paper, $v$ is taken as 7 m/s. To prevent the anchor from sliding during the anchor smashing process, the movement of the anchor in the x and z directions is constrained so that the anchor can only move in the y direction. Since the anchor damage failure only occurs locally in the submarine cable, the length is much smaller than the total length of the submarine cable, so the two sections of the submarine cable can be completely fixed with the bottom end on the soil.

#### 3.2. Finite Element Simulation Results

## 4. VMD-Volterra-SVM Algorithm Validation

#### 4.1. VMD Decomposition and Feature Extraction

^{−7}, the decomposed modal components are obtained, and the waveforms of each modal component are shown in Figure 5. The horizontal axis represents time, measured in seconds, while the vertical axis represents the magnitude of the acceleration. From Figure 5, it can be seen that the VMD decomposition results are more reasonable and can effectively suppress the modal mixing phenomenon.

#### 4.2. Fault Identification Results and Analysis

## 5. Conclusions

## Author Contributions

## Funding

## Data Availability Statement

## Conflicts of Interest

## References

- Zhao, Z.H.; Zheng, Q.Z.; Sun, T.X.; Huang, Y.H.; Li, H.J. Submarine cable fault location system and method based on optical fiber pulse transmission. Electr. Meas. Instrum.
**2020**, 57, 24–29+87. [Google Scholar] - Lv, A.Q.; Li, J. On-line monitoring system of 35 kV 3-coresubmarine power cable based on phi-OTDR. Sens. Actuators A Phys.
**2018**, 273, 134–139. [Google Scholar] [CrossRef] - Zhang, X.; Yin, C.Q.; Lv, A.Q. Method of Constructing Finite Element Model and Simulating of Photoelectric Composite Submarine Cable. Comput. Simul.
**2013**, 30, 120–124+147. [Google Scholar] - Wang, Y.; Zhou, B.D.; Lin, X.B.; Li, S.Q.; Hu, K.; Lv, A.Q. Anchor Damage Detection of Submarine Power Cable based on Distributed Optical Fiber Vibration Sensing Technology. Study Opt. Commun.
**2018**, 2, 40–43. [Google Scholar] - Zhang, Z.P.; Meng, S.X.; Hu, L.X.; Huang, X.Y.; Wang, S.H.; Li, T. Influence of Anchor Damage on Structure Layer of 500 kV Submarine Power Cables. High Volt. Eng.
**2020**, 46, 561–568. [Google Scholar] - Shang, Q.F.; Gong, B.; Zheng, G.Q. Analysis of vibration Characteristics of Optical Fiber Composite Submarine Cable under Anchoring. Study Opt. Commun.
**2021**, 5, 45–49+56. [Google Scholar] - Zheng, G.Q. Research on the Vibration Signal Analysis Method of Optical Fiber Composite Submarine Cable Based on ESMD and SVM. Master’s Thesis, North China Electric Power University, Beijing, China, June 2021. [Google Scholar]
- Konstantin, D.; Dominique, Z. Variational Mode Decomposition. IEEE Trans Signal Process.
**2014**, 62, 531–544. [Google Scholar] - Wei, R.X.; Han, C.Z.; Zhang, Y.Y.; Kong, X.Y.; Song, Z.P. Volterra model method for fault diagnosis of a nonlinear system. J. Syst. Eng. Electron.
**2004**, 11, 1736–1738+1752. [Google Scholar] - Zhang, C.; Zhao, R.Z.; Deng, L.F. Weak fault identification of rolling bearings based on VMD singular value entropy. J. Vib. Shock.
**2018**, 37, 87–91+107. [Google Scholar] - Fouda, B.M.T.; Yang, B.; Han, D.Z.; An, B.W. Pattern Recognition of Optical Fiber Vibration Signal of the Submarine Cable for Its Safety. IEEE Sens. J.
**2021**, 21, 6510–6519. [Google Scholar] [CrossRef] - Jiang, X.X.; Song, Q.Y.; Du, G.F.; Huang, W.G.; Zhu, Z.K. A review on research and application of variational mode decomposition. Chin. J. Sci. Instrum.
**2023**, 1–24. [Google Scholar] - Yang, G.Y.; Ding, X.N.; Wang, J.Q.; Wei, Y.D.; Zhou, X.L. Rotor fault diagnosis method of singular value entropy of Volterra modal based on VMD. Manuf. Technol. Mach. Tool
**2022**, 3, 150–156. [Google Scholar] - Yang, Y.F. Applications of Empirical Mode Decomposition in Vibration Analysis, 1st ed.; Defense Industry Press: Beijing, China, 2013; pp. 82–98. [Google Scholar]
- Xu, Y.Q.; Zhou, C.; Geng, J.H.; Gao, S.G.; Wang, P. A Method for Diagnosing Mechanical Faults of On-Load Tap Changer Based on Ensemble Empirical Mode Decomposition, Volterra Model and Decision Acyclic Graph Support Vector Machine. IEEE Access
**2019**, 7, 84803–84816. [Google Scholar] [CrossRef] - Li, D.Z.; Zheng, X.; Xie, Q.W.; Jin, Q.B. A sequential feature extraction method based on discrete wavelet transform, phase space reconstruction, and singular value decomposition and an improved extreme learning machine for rolling bearing fault diagnosis. Proc. Inst. Mech. Eng. Part E J. Process Mech. Eng.
**2018**, 232, 635–649. [Google Scholar] [CrossRef] - Yu, T. Research on Identification of Voltage Sag Source Based on IVMD and M-SVM. Master’s Thesis, Liaoning Technical University, Huludao, China, June 2019. [Google Scholar]
- Hu, Y.J. Research on Finite Element model of Optical Fiber Composite Submarine Cable Mechanical Behavior. Master’s Thesis, North China Electric Power University, Beijing, China, March 2018. [Google Scholar]
- Feng, Y.S.; Shang, Q.F.; Lv, A.Q. Dynamic Finite Element Analysis of Fiber-Optic Composite Submarine Cable Under Wave. Study Opt. Commun.
**2017**, 4, 30–34. [Google Scholar]

**Figure 4.**Vibration acceleration curve of the submarine cable. (

**a**) Vibration acceleration curve at the moment of anchor smashing; (

**b**) vibration acceleration curve at the moment of scouring.

**Figure 5.**The VMD decomposition waveform of a submarine cable vibration signal. (

**a**) Scouring vibration signal decomposition; (

**b**) anchor smash vibration signal decomposition.

Submarine Cable Status | Sample | IMF1 | IMF2 | IMF3 | IMF4 | IMF5 | H |
---|---|---|---|---|---|---|---|

Scrubbing | Sample 1 | 2.5037 | 1.1586 | 0.6795 | 0.3894 | 0.1958 | 1.5193 |

Sample 2 | 2.5023 | 1.1659 | 0.6775 | 0.3954 | 0.1965 | 1.5237 | |

Sample 3 | 2.5113 | 1.1548 | 0.6804 | 0.3904 | 0.2005 | 1.5272 | |

Anchor smash | Sample 1 | 2.3902 | 1.0962 | 0.5535 | 0.2973 | 0.1159 | 1.2056 |

Sample 2 | 2.4037 | 1.0804 | 0.5221 | 0.2932 | 0.1522 | 1.2061 | |

Sample 3 | 2.3954 | 1.0965 | 0.5361 | 0.2896 | 0.1561 | 1.2105 |

Hyperparameter | Size | Hyperparameter | Size |
---|---|---|---|

Quadratic penalty factor α | 2000 | Convergence parameter ε | 10^{−7} |

Lagrange multiplier step τ | 0 | Penalty parameter | 3.568 |

Number of IMF decomposition K | 5 | Non-negative relaxation factor ζ_{i} | 2.248 |

Confusion Matrix | True Value | |||
---|---|---|---|---|

Scrubbing | Anchor Smash | |||

Predicted Value | VMD | Scrubbing | 20 | 0 |

Anchor smash | 0 | 20 | ||

EMD | Scrubbing | 17 | 2 | |

Anchor smash | 3 | 18 | ||

EEMD | Scrubbing | 19 | 1 | |

Anchor smash | 1 | 19 |

Disclaimer/Publisher’s Note: The statements, opinions and data contained in all publications are solely those of the individual author(s) and contributor(s) and not of MDPI and/or the editor(s). MDPI and/or the editor(s) disclaim responsibility for any injury to people or property resulting from any ideas, methods, instructions or products referred to in the content. |

© 2023 by the authors. Licensee MDPI, Basel, Switzerland. This article is an open access article distributed under the terms and conditions of the Creative Commons Attribution (CC BY) license (https://creativecommons.org/licenses/by/4.0/).

## Share and Cite

**MDPI and ACS Style**

Zhu, W.; Fan, C.; Xu, C.; Dong, H.; Guo, J.; Liang, A.; Zhao, L. Anchor Fault Identification Method for High-Voltage DC Submarine Cable Based on VMD-Volterra-SVM. *Energies* **2023**, *16*, 3053.
https://doi.org/10.3390/en16073053

**AMA Style**

Zhu W, Fan C, Xu C, Dong H, Guo J, Liang A, Zhao L. Anchor Fault Identification Method for High-Voltage DC Submarine Cable Based on VMD-Volterra-SVM. *Energies*. 2023; 16(7):3053.
https://doi.org/10.3390/en16073053

**Chicago/Turabian Style**

Zhu, Wenwei, Chenyang Fan, Chenghao Xu, Hantuo Dong, Jingen Guo, Aiwu Liang, and Long Zhao. 2023. "Anchor Fault Identification Method for High-Voltage DC Submarine Cable Based on VMD-Volterra-SVM" *Energies* 16, no. 7: 3053.
https://doi.org/10.3390/en16073053